Model : S-PL0606-S15-EMG
- Keep working when the power cut off
- Emergency time 1/1.5/2/3 hours
- Easy for installation and set up
Dimension : 603x603mm , 1203x303mm , 1203x603mm , other sizes can be customized
LED Chip : San'an / Philips / Osram option
Norminal Power : 25W-72W
Luminous Flux (LM) : 100lm/w / 120lm/w / 130lm/w / 140lm/w / 150lm/w / 160lm/w option
CCT : 2700k / 3000K / 4000K / 6000K / 6500K option
CRI : Ra>80 , Ra>90 , Ra95 , Ra97 , full light spectrum option
UGR(Unified Glare Rating) : UGR<23 , UGR<19 , UGR17 , UGR16 option
Materials : Aluminum frame , PMMA LGP
IP Rating: IP40/IP44/IP54/IP65 options
Lifetime : 50000H
Warranty : 5 years
Working Ambient Temp. : -20~+40℃
Working Ambient Humidity : 10%~90%
Mounting : Recessed , Suspending , Surface mounted , Spring clips , T-bar
Dimmable : On/Off / Push / Triac / 0-10V / 1-10V / DALI dimming
Certificate : ETL , DLC , FCC
Emergency power supply
Input Voltage : AC110V-277V , 50/60Hz
Emergency watt : Max 10W (10%-100% can be adjustable)
Battery capacity : 14.4V (28.8WH)
Emergency maintenance time : >90 minutes
Power factor ≥90%
Emergency switch time ≤ 1S
Lighting system : continuous
Battery warranty : 2 years
Commercial areas , Industrial areas , Office , Meeting room , Reception area , Shop , Retail , Supermarket , Corridor , Bank , etc .
1.This emergency product should be installed by trained electricians. Forbid connecting wires when power is on, make power on after make sure that there is no phenomenon of short circuit and the correction isok.
2.Mainpowerline:LivewireTLandnulllineN,connecttomainpowerlinedirectly. no switch can be allowed when emergency lighting. the law forbids the switch control emergency circuit.
3.The wall switch only controls the main power, no function on emergency lighting. The Switch live wire SL and charging live wire TL should be in the same phase.
4. Green light-main power , Red light-charging ,Yellow light-mulfunction, Test: test button .
5.Emergency lighting condition,three-color light is all out.
6. Digital circuits, self-test function (monthly inspection, annual inspection), fault or automatic alarm function cause by illegal operation.
7 .You should connect the led lamp and charge the emergency pack before use. In order to avoid emergency lighting function failure.
8 .The environment temperature of Emergency pack ranges from minus ten degrees centigrade to 50 degrees centigrade. High-temperature aging test is forbidded.
9 .Frequently test is prohibited . Each test interval is not less than one minute.
10 .Emergency movement is the core device which controls the battery charge or discharge and start the lighting when under emergency must ensure the wiring is correct. After under normal use, need to discharge once every three months for battery conservation and extend the battery life. Emergency lighting power installed and put into use, need to regularly check, maintain, examine and repair when discover the abnormal condition, or inform the supplier to deal with.